Chiller Maintenance works in London
When it comes to Chiller Maintenance, chillers contain hundreds of kilos of refrigerant gases that require regular leak check tests. Regular leak checking can prevent costly refrigerant replacement works. It is critical to ensure that only an F-gas qualified professional carries out these works, furthermore, it is also a legal obligation to record a mandatory log for all of the plant on your site containing refrigerant gas.
Watch the video below of our engineers performing a major Chiller Maintenance in London. Our engineers follow a detailed planned maintenance schedule performing checks and logs across all the chiller components. In the featured chiller works, due to visible signs of refrigerant oil leaks, we performed the following remedial works:
- Reclaimed and weighed refrigerant from all circuits
- OFN Pressure leak testing
- Oil Sample analysis of each circuit
- Replacement Parts: Liquid Line Filter Drier Core, Oil and Oil filter
The chiller was operating with inadequate water flow found as part of our simultaneous Chilled Water Balancing works.
In most cases, a chiller maintenance engineer would look at the chiller circuits alone, however, our engineers are CIBSE trained in water balancing, giving us the edge when performing your Chiller Maintenance works.
The chillers cooling demand, is dependent on the closed water circuit flowing through the chiller. The water, cycles through a constant pumped flow and return circuit set at a desired set point. In the case here, the water flows through the chiller evaporator set point of 5c, providing chilled water to air handlers and fan coil units.
Maintaining the chilled water design flow
Maintaining the chilled water design flow in line with the chillers required flow is essential. Low water flow issues could cause the chiller evaporating pressures to drop and cut out the chiller. It is equally important to ensure the water itself contains an anti freezing Glycol additive. This particular chilled water circuit has additional, low outdoor ambient heating elements on the external pipe work, therefore, reducing the chances of the water freezing within the pipework.
HOW OFTEN IS YOUR CHILLER LEAK TESTED?
Chiller maintenance leak testing is an essential part of planned preventative maintenance. Chiller’s contain pressure devices that in the event of abnormal pressure readings, they will cause the chiller to shut down.
When chiller condenser coils are not regularly cleaned, blockages cause high pressure. This could also occur if condenser fans were to fail. Pressure cut out devices sometimes also become faulty, resulting in the last fail safe of releasing high pressure gas through the pressure release valve. The pressure release valve is the last fail safe that protects the system from major compressor damage, explosion of pipe and connected devices. The pressure release valve is a mechanical device that will activate at a pressure set point. When the pressures rises above the PRV (pressure release valve) allowance pressure it will dump the chiller gas until the pressure falls back to normal.
Maintenance contract customers receive exclusive rates on chiller maintenance!
Save on costly Chiller Repair works and get your chiller covered under contract with us today.
Don’t leave yourself held to ransom in the event of an emergency breakdown , with high peak season quoted costs! Get in touch with our team today to arrange your maintenance contract for all of your Chiller Maintenance needs.
As a chiller maintenance customer of ECS we offer fixed call out rates, as-well as our 24hr manned phone lines, this ensures you get the help that you require.
Call us today for more information on our maintenance contract rates!